- Posted by
5 Reasons You May Have Slow Flow Rates From Your Reverse Osmosis System
Updated Oct 15, 2020
- Clogged RO Filters: If you forget to change your water filters, with time your system will produce less and less water. Clogged or fouled RO water filters is the most common reason for a slow-filling RO tank and faucet flow. Trying to fill a reverse osmosis water tank with a fouled membrane may take 4-6 hours, rather than the usual 2-4 hours. You may want to set a calendar alarm so you'll remember to replace your filters on time. To order filter replacements, learn how to find the correct filters for your system. And to simplify annual filter replacements, we've created filter bundles. Start of selecting your brand and model to determine available filter replacement kits.
- Pressure in Tank: You might have low air pressure inside the RO tank itself. Your tank should have pressure of 7 to 8 psi without any water in the tank. To check your pressure, locate the Schrader valve, typically covered by a blue plastic cap, on the side of the tank near the bottom. After removing all the water from the tank, use a low pressure gauge to determine the pressure in the tank. If low, add air with a pump until you have 7-8 psi. Be careful to only add a small amount of air at a time, as too much pressure can rupture the air bladder. For more water pressure tank troubleshooting, check out our Reverse Osmosis Troubleshooting Guide>.
- Ruptured RO Tank Bladder: If you only get about 8 ounces (one cup) of water out of your RO faucet at normal water pressure, and then the water instanty trickles down to a very small stream, this typically is a sign the air bladder in the storage tank as ruptured. Bladder tank problems unfortunately cannot be repaired. The only way to resolve the issue is to replace the storage tank. Replacement tanks can be found here.
- Kink in water line: Make sure there are not any kinks in the water line, which would slow water production. And while you're inspecting your system, double check that the water supply line valve is in the fully open position.
- Temporary Loss of Water Pressure: You may have temporary loss of water pressure with your local utility company. An RO system needs a minimum of 40 psi to operate properly, but 60 psi is optimal. If all of your household faucets seem to have low water pressure, then most likely your utility company is temporarily flowing water at a lower pressure. Often, higher water pressure will return if you wait a bit. If higher water pressure does not resume, report the issue to your local water utility company.
If none of the above seem to be the issue, consult our troubleshooting guide or call a water treatment specialist in your area. For products purchased through espwaterproducts.com, customer support is available Monday through Friday 8 am to 5 pm (Central) at 877-377-9876. Have your customer or invoice number ready.
Again, make filter changes easy for yourself with "filter bundles" that include everything you need for annual filter replacements. These bundles simplify filter changes and often save you money. Find your filter bundle by identifying your RO system brand/model.
We installed the Hydro Guard Reverse Osmosis drinking water system August of 2018. Now that it's been installed and in use for some time, I can give a pretty candid review of this reverse osmosis system. Quick Look at the Hydro-Guard Reverse Osmosis System: I like the convenience of having clean, filtered, great-tasting, drinking water right at my kitchen [...]
Do I Need a Whole House Reverse Osmosis System? If you like the water produced by your reverse osmosis drinking water system at your kitchen tap, wouldn’t it make sense to install a whole house RO system? Maybe not! Here's why Whole House RO May not be the Right Choice: RO has its' place in the water filtration [...]
The majority of Americans are concerned about the overall quality of their water supply. A 2019 study of consumers' opinions and perceptions regarding water quality, looked at Americans’ attitudes and concerns about their water. It is the seventh time in 15 years that the Water Quality Association (WQA) has commissioned this professional opinion research team.Among the major [...]
Do RO Water Filtration Systems WASTE Water? If you have dirt on your hands and use water to rinse off the dirt, are you wasting water? Most would say no, but using water to wash the hands. Simply put: in the Reverse Osmosis process, water is utilized to "wash" impurities out of your water, too. Yes, water [...]
How to Find & Order RO Replacement Filters: So it's time to replace the filters for your Reverse Osmosis water filtration system. Figuring out which filter or membrane you need to purchase can be overwhelming. Get started by determining the brand of model of your RO filter system. Tips to Determine Brand and Model of RO System The most [...]
Reverse Osmosis Tank Not Filling Up? If your Reverse Osmosis tank won't fill and you're wondering how long it normally takes to fill an RO tank, the short answer is it typically takes 2 to 4 hours to fill a standard reverse osmosis holding tank (2.8 gallons or 10.6 L). Because the reverse osmosis filtering process takes [...]
How to Select a Home Water Filter System Figuring out which water filtration system you need can be a daunting task. By thinking through and answering the following five questions, we can help you determine which system is right for your household.1. Whole House vs. Under Sink Drinking Water Filter? There are basically two different types of [...]
Many of our customers who purchase an under-counter Reverse Osmosis water filtration system choose to install the system themselves. Yes, DIY is becoming increasingly popular, so when folks call in and ask about self installation, we generally answer, If you're handy and somewhat mechanical, installing an RO system should not be too difficult or time consuming. By [...]
Why UV Water Treatment?If your home receives water from a city or municipal water supplier, you may be asking, "Do I need an ultra violet water filter system?" After all, why should you worry about additional water treatment if the water has already been treated at a water plant? Municipal water suppliers do their best to protect [...]